Writer： admin Time：2021-09-17 00:00 Browse：℃
The fuel of the biomass burner is a waste wood and crop waste to compress the raw material to the same biomass wood particles like feed particles. The biomass particles are fed into the combustion chamber for direct combustion, then the imported burner is turned off. Method
Import burner running flameout solution
After the burner is running, after the fire is successful, start the operation, start the ignition, the fire is turned on, but the fire is running is normal, but after the operation is about 30RAIN, suddenly turn off the fire, restart, the fan operation, the blow action is normal, but I can't ignite. (1) Troubleshooting. By looking for the reasons for the water supply, there is a natural gas pipeline, which is caused by water, so it is pulled with the pipeline and repeatedly purge the pipeline until it is completely treated with the water, and the test is reacting. Operating normally. & # 65279; The above reason is that the construction unit has not discharged clean water in the water pressure test of the natural gas pipeline, causing aqueous gas into the valve group and forms water, hinders the internal solenoid valve rod action, Natural gas cannot enter the burner nozzle through the valve group, causing a failure that cannot be ignited. Imported low nitrogen burner (2) fault judgment. Causes of unable to ignition failure include instrumental system problems; air supply system problems; gas gas path issues. By checking the gas path, it is found that one dedicated gas valve group is installed in the end of the gas pipeline. The interior is composed of one set of alarms by one filter for 1 filter. It is controlled to control the gas disconnection and secondary reduction. The role of pressure and leakage, the valve group is an exclusive design, sophisticated structure, affordable, and is one of the core components of the boiler. Its front-end pressure & lt; 70kpa, the rear end pressure experience is 4 kPa. When the front and rear end pressure test of the valve group is found to be almost 0, it is determined that the inner solenoid valve in the valve group is not opened. After the discharged valve group, about 100 ml of water flows out from the bottom cover, open the filter sewage valve, after the water is released, and the hair dryer is dried, and the reduction is reduced.
Add: No.33 Xinhua Road,Xinmi,Zhengzhou,China